All electrical installations in new buildings and renovations require electrical permits. A certified electrical contractor must apply for and complete the work. To be eligible to apply for contractor electrical permits, you must:
Many common questions about electrical permits can be answered by The City’s Technical Assistance Centre. Inquiries about building, plumbing, electrical or heating, ventilation and air conditioning code or construction methods, building safety and fire regulations, please contact the Technical Assistance Centre. If you would like to contact a specific inspector, view the
Electrical contact list.
In some cases, homeowners may apply for permits if they own and live in the home and are completing the work themselves. Under the same criteria, homeowners, who reside or intend to reside in their home, can now apply for electrical and plumbing permits for approved secondary suites. There are no required drawings or forms to apply for electrical and plumbing permits; simply bring ID, proof of ownership (in cases where the property has been purchased recently) and a cost estimate to the Planning Services Centre, located on the 3rd Floor of the Municipal Building.
For more information, view the Homeowner electrical wiring guide and Homeowner's electrical permits, or contact the Planning Services Support Centre at 403-268-5311.
Secondary suite electrical load calculation
Are you developing a secondary suite or laneway house? Use the secondary suite electrical load calculation sheet to make sure your current electrical service is adequate. When completed, please submit the form to firstname.lastname@example.org. If it has been determined that the main electrical service has to be increased from a 60 amp, 100 amp or 200 amp service, please contact ENMAX.
Please also note that all plumbing services, including sanitary, storm and water, must be verified onsite by the owner or builder to ensure the size and location is compliant with the National Plumbing Code of Canada for the number of fixtures being installed. The waterline must be of the size that is indicated on the grade slip, but not smaller than 1 inch.
Underground service conductor installations
Beginning April 1, 2016, contractors will be required to
submit plans for the underground service conductor installation, as specified in
the Canadian Electrical Code or as calculated by the IEEE 835 standard, when
the permit is initially obtained. These plans are required for commercial, commercial
– multifamily and industrial sites where the service conductor sizes are 1/0
and larger. By reviewing the plans proactively, we are able to ensure the Canadian
Electrical Code standards are being met from the get-go and prevent issues
arising later on.
The IEEE835 standard does not apply to installations located in the downtown core and supplied from the ENMAX network.
For more information, contact 311 and ask for the Technical Assistance Centre (TAC).
- Electrical Permit
- Fire Alarm (Electrical Permit and Building Permit required)
- Annual Permit
- Single Construction Permit (issued to builder)
Additional permits may be required for solar, factory built structures (skid units), hot tubs, air conditioning units, garages, sheds and more.
An Annual Permit is required if your establishment employs a full time electrician. An electrical contractor that is doing maintenance work at a facility may also apply for an Annual Permit.
A separate permit is required for each commercial tenant space; and units of multiplex, row housing, townhouses and or condominium/condominium apartments.
Submission of plans and drawings:
The Electrical Inspection Section requires plans and drawings for new construction or service upgrades on services of 600 amps and larger and all high voltage installations.
A single Line Diagram and Manufacture Shop Drawings are required to be submitted with the following information included:
- Fault current at all over-current devices
- Service characteristics and all ratings of over-current devices at all service and distribution equipment
- All panels and over-current devices to indicate if series-rated combination is used
- Check off sheet from link included with permit confirmation email
The shop drawings may be emailed to The City of Calgary at email@example.com.
Requesting an inspection
Inspection appointments are booked by contacting 311. Requests for an inspection must be made between 8 a.m. and 2 p.m.
When requesting an inspection, please provide:
- Permit number (eg. BPYEAR-00000, EPYEAR-00000)
- Job address
- Type of inspection (eg. final, rough, progress, underground, service and occupancy)
- Inquiries regarding specific jobs may be referred to the area inspector.
- For problems that cannot be resolved with the area inspector, or if the area inspector is not available, please contact the Senior Inspector.
- Inquiries regarding plans can be made by contacting 311 and asking for the Technical Assistance Centre - Electrical.
The Safety Codes Act allows variances to requirements in regulations and codes adopted under the Safety Codes Act. Refer to the Electrical Variance form
to request a variance.
Energizing of services
Electrical services (except single family) will not be energized unless they have been inspected and labelled.
Illegal bypass of meter
When Electrical Service Conductors are purposely damaged to bypass the Electrical Service Meter or the main over-current device, the service conductors must be completely replaced to the point of connection to the electrical utility power supply. Damaged underground cables must be replaced to the property line and damaged overhead conductors must be replaced to the weatherhead. For extenuating circumstances where the service conductors cannot be removed or replaced, permission from the Electrical Inspection Section is required.
Temporary construction services
All temporary services, regardless of size, are to have a HRC fused disconnect switch in front of the meter. Enmax will not energize any HOT Sequence metered Saw Service.
Main service panelboard without a main disconnect
Sub-panels cannot be added to an existing service panelboard that does not have a main disconnecting device. These panelboards were originally approved for installation where the number of branch circuits was limited.
Working on energized electrical services
On underground services where repairs or alterations are required on the line side of a hot sequence utility meter, contact ENMAX first line response at 403-514-6000. Reconnection will be completed, provided a permit has been issued.
On overhead services, the utility service drops may be disconnected at the service head and temporarily reconnected when work has been completed. They may also be temporarily reconnected; however only when using the required and approved splicing method.
When repairs or alterations are required on the load side of a hot sequence utility meter, the meter may be removed.
Please contact ENMAX prior to beginning work.
Overhead services (residential infill dwellings)
Please ensure that the exposed service conductors that are not higher than windows, doors and porches. Clearance must be 1 metre or more. The service attachment point shall not exceed 5.5 metres from finished grade level.
When installing services in a floodway or floodplain, the main electrical service must be installed above the flood level. Check with a general contractor to see if you are on a floodway or floodplain.
Please check that your electrical rooms comply with Rule 2-310 of the Canadian Electrical Code. For services rated 1200 Amp or more, or over 750 Volts, a working space of 1.5 metres is required.
Existing hot splitters (commercial)
When a load is added to an existing hot splitter, the following applies:
- A disconnect switch marked, “Suitable for Service Entrance Equipment” shall be installed between the existing splitter and the utility service drops. The switch will be called a “Service Supply Disconnect Switch.”
- The disconnect switch is to be either a standard enclosure, protected by a metal cabinet with metal doors, or an Enclosure Type 3R for outdoor use.
- The disconnect and metal raceways will be grounded by using the neutral conductor for bonding all metal parts.
- The disconnect is to be protected from mechanical damage where installed in alleys or similar locations.
- Fuses shall be sized to the ampacity of the existing splitter or service conductors, whichever is smaller, and shall be of a HRC type fuse.
Breakers should not be installed and terminated on the rough-in stage of construction because these circuits are being accidentally energized. This has resulted in flashes in outlet boxes and contact with energized wires. We do not recommend this procedure.
Hydro massage bathtubs
Acceptable forms of access to pump motors are:
- Removable panels.
- Removable one-piece skirts, provided they are friction fit and are siliconed around the perimeter.
- Removable section of the tub skirting with visible screw holes.
Underground inspections – Single Construction Permit application only
All underground inspections must be notified for inspection.
The Safety Codes Officer will conduct periodic spot checks of underground installations on single family and semi-detached dwellings.
Violation of the current installation practices will result in the electrical contractor being placed on notice. Any recurring violations may result in withdrawal of backfilling privileges.
If backfilling occurs while the electrical contractor’s privileges have been withdrawn, the underground installation will be exposed at the contractor’s expense.
As a general guide, the rigid PVC conduit from the coil location to the meter base should be sized as follows. Please keep number of bends to a minimum.
53 mm (2 in)
2 – 2/0
63 mm (2.5 in)
3/0 – 4/0
Installation of decorative Christmas tree lights in public areas
The Electrical Inspection Section has received a number of requests to investigate incidents where citizens have received electrical shock from the lighting of Christmas trees.
Generally, incidents have occurred where lights have been installed in public areas and the lamp was damaged, leaving exposed live lamp filaments.
To alleviate the problem, we recommend that all decorative Christmas tree lighting below 2.1 metres (82.5 inches) installed in areas accessible to the general public be on a circuit protected by a Ground Fault Circuit Interrupter of the Class A type.
Please contact 311 if further information is required.
Information and forms